HVAC Services & AC Repair & Installation in Scottsdale, AZ
Since 2015, All Out Cooling & Heating has been setting a high standard for the HVAC industry in Scottsdale, AZ. We build customers for life through honesty & fair prices. We look forward to the opportunity to become your trusted HVAC solution. From air conditioning services to home heating, we are passionate about providing only the best for your home. We also offer ductwork services and air filtration solutions to help you breathe fresh, clean air indoors. We look forward to the opportunity to become your trusted HVAC solution.
Our Staff Is Highly Trained & Always Courteous
We are fully licensed, trained professionals. We will help relieve any stress you have over your HVAC issues. Our friendly, courteous office staff and knowledgeable technicians will put your worries at ease.
We are dedicated to delivering an HVAC service you will be happy with & tell your friends, neighbors and coworkers about. Along with having all professional licenses required by the state of Arizona, we have tons of 5-star reviews that have built our reputation as one of the most trusted HVAC companies in Scottsdale.
We Offer Great Prices on Top Brands
We only represent the industry’s best, most reputable brands. No matter what type of HVAC issue might need a repair or replacement, every part we use comes with the highest-rated warranties and guarantees in the business. When you need local service you can trust, give us a call at 480-578-1370 to schedule!
Recent Jobs and Reviews in Scottsdale, AZ
Job Locations and Reviews
Need to provide estimate for replacing a patio roof. It's 10'x15'. Need 2x6x10 boards, plywood and roofing roll out.
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6E7D-14878B7B76C648D9B5206CC9996F8D13
Upon arrival found thermostat need to be adjusted to hp to de activate the reversing valve The unit is now heating
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6E7D-26E364751C2F4774899BCE90BD99DADA
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-3F0D3F38CE8A44269FE10CC54E4F1EEA
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-537943EEC97D48D3AC7A2AAD2C593548
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-AF6050BE0E0B4D12A45CDE509E9EC9FF
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-8CBD79BFA5864713A1511D7160215B3F
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-4618A2A8EF5244519048C5F3FEFAA170
Service call from a client who was experiencing water leaks around their HVAC unit. After a thorough inspection, I identified a clogged drain line as the culprit. I cleared the blockage, preventing further water damage, and ensuring the unit's condensate could drain properly. The client's home is now free from water leaks, maintaining a dry and comfortable indoor environment, and the risk of potential water damage has been eliminated.
Upon arrival completed tune ups found some bad caps in the four tone unit.talked to customer she did not want to do any repairs. George will come out Wednesday between 12 and four to come talk to customer about replacement of the unit as she requested.
Completed AC maintenance on one package unit on upstairs balcony. Completed maintenance checklist and unit information. Found system working correctly at this time. Anita would like to sign up on our maintenance package.
Made repairs in estimate and checked operation. System now cooling correctly.
Found grounded compressor. (2stage is now 1 stage per manufacture). Must replace grounded compressor, capacitor, drier and contactor. Will give replacement refrigerant price if necessary. If not necessary will only charge for refrigerant reuse.
Found condenser with delay faulty. Re wired to remove delay. Found system R22 low on charge. Found faulty contactor. System needs to be changed please send George. Can not deliver quote due to system low on charge and it’s R22. System now cooling but could have problems at any moment. From 1995.
3 ton Daikin package heat pump 2 stage compressor 15.2 SEER2 System qualifies for SRP rebate of $450 ($150 per ton). SRP will send you a check 4-8 weeks after completion of install. System comes with a 12 year parts warranty 6 year unit replacement through Daikin. 2 year labor warranty through All Out. Scope of work: 1. Remove & Replace existing package heat pump system with new AHRI rated package heat pump system. 2. Crane Included for Installation. 3. Supply & Install new service disconnect & electrical whip. 4. Supply & Install new double pole breaker at electrical panel. 5. Supply & Install new insulated transition. 6. Supply & Install new redwoods for unit to sit on. 7. Supply & Install new thermostat control 8. Supply & Install new primary drain p-trap and test for proper operation. 9. Disposal and haul away of existing equipment per E.P.A. guidelines. 10. Process applicable utility rebates. 11. Register equipment to activate extended warranties. 12. Final site visit by Ins
Upon arrival turned unit on at the thermostat. all functions are working at this time. the unit is turning on and turning off as per manufacture specs. the air coming out of the vents is Luke cold. leading me to believe there is a refrigerant issue. unable to check refrigerant pressures due to leak lock on the refrigerant caps. George is going to come by tomorrow.
Found system with err114 at trane comfort link thermostat. Found broken p trap and not leveled correctly. Reset unit, re plumbed system and found system working correctly at this time.
Found restriction at indoor txv at air handler in closet. Found txv and filter drier under warranty. Went to pick up part and tools to complete job. Returned to job, pumped down system and replaced txv and liquid line drier. Released refrigerant and checked operation. Found system charged correctly with 8degree sub cooling and 19 degree split. System working correctly at this time. Found restriction at indoor metering device (txv). Need cover, replace txv and filter drier and re charge per manufacture specifications
Completed Pma cooling visit on one package unit on roof. Completed Pma form. See form for maintenance details. System cooling properly at this time. Logged model and serial number into service titan.
Install 4x4 cover plate at electrical box. Insulate water valve that’s leaking down onto cover. Clean fan motor, blower cage and indoor coil. Thursday august 10. Returned to preform quote repairs. Installed 4x4 plate over exposed electrical box that was flagged during inspection. Insulated cold water pipe that was dripping water down onto return. Cleaned indoor coil and blower. Found system cooling with 10 degree split at this time. The cooling tower comes from the building. Went to the office of the building and was told that there is a known issue with the cooling tower. Air flow is much better after cleaning was done but system not cooling as well as it should due to lack of cold water from building cooling tower.
Perfromed service on fan coil. Found fan coil in unit with dirty fan and coil in need of cleaning. Found 4x4 plate missing at electrical box and water valve needs to be insulated. Spoke with Ben about repairs and emailed quotes. He asked that we schedule this work asap.
System comes with a 12 year warranty and 6 year unit replacement through Daikin. 2 year labor warranty through All Out. Scope of work 1. Protect home with floor covers. 2. Remove & Replace existing split system with new AHRI rated split system with air handler in closet or garage. 3. Supply & Install new custom fabricated duct transition sealed to the flange of the air handler to prevent air leaks. 4. Supply & Install condensate safety switch. 5. Supply & Install new condensate EZ-trap with cleanouts and brush for ease of maintenance. 6. Supply & Install a heavy-duty electrical cord or service disconnect for the air handler. 7. Supply & Install a new smart thermostat. 8. Supply & Install new service disconnect & electrical feeder from disconnect to system. 9. Supply & Install a new fused disconnect that is properly rated for the new outdoor system. 10. Flush existing line set to remove debris and mineral oil in preparation for R410a refrigerant. 11. Purge nitrogen throug
Found system not cooling upon arrival. Found weak capacitor for compressor. Replaced capacitor and checked operation of equipment. System now cooling properly at this time. Replace compressor capacitor
System not cooling, Found faulty dual run capacitor at outdoor condenser faulty. Changed capacitor 80/5 and checked operation. System cooling properly at this time. Part is likely under warranty, will search this coming week and send Denny the bill.
Thank you for taking the time to leave such a positive review! We're glad to hear you had a great experience with us.
Barbara, we're so happy that you're pleased with the service we provided. Thank you!
Houston, thank you for choosing us to replace your air ducts. And thank you for this great review of our team!
Leah, thank you for this great feedback! And thank you for trusting us with all of your HVAC needs!