HVAC Services & AC Repair & Installation in Phoenix, AZ
Since 2015, All Out Cooling & Heating has been setting a high standard for the HVAC industry in Phoenix, AZ. We build customers for life through honesty & fair prices. We look forward to the opportunity to become your trusted HVAC solution. From air conditioning services to home heating, we are passionate about providing only the best for your home. We also offer ductwork services and air filtration solutions to help you breathe fresh, clean air indoors. We look forward to the opportunity to become your trusted HVAC solution.
Our Staff Is Highly Trained & Always Courteous
We are fully licensed, trained professionals. We will help relieve any stress you have over your HVAC issues. Our friendly, courteous office staff and knowledgeable technicians will put your worries at ease.
We are dedicated to delivering an HVAC service you will be happy with & tell your friends, neighbors and coworkers about. Along with having all professional licenses required by the state of Arizona, we have tons of 5-star reviews that have built our reputation as one of the most trusted HVAC companies in Scottsdale.
We Offer Great Prices on Top Brands
We only represent the industry’s best, most reputable brands. No matter what type of HVAC issue might need a repair or replacement, every part we use comes with the highest-rated warranties and guarantees in the business. When you need local service you can trust, give us a call at 480-578-1370 to schedule!
Recent Jobs and Reviews in Phoenix, AZ
Job Locations and Reviews
Upon inspection I found a bad transformer on 3 heating units. Replaced transformers and added a 5 Amp fuse for protection. All 3 heaters are working properly at this time.
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6E7D-80942271D79C46E388A96163270AB100
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6E7D-37A1CE2A4E56476183512C40DB34B7CC
Upon arrival conducted routine maintenance on the unit also ran PVC from current spot over to edge of roof on the other side to get it away from the travertine
Upon arrival found bad XR 13 motor replaced with a new XR 13 motor unit is now running within spec.
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-C5DAA93525234D46AA89A7CD80432F26
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-387D30B7260444508771444153DCE3E7
Corn rival found in nature fan motor wires were dropped off from the condenser fan replaced with a new condenser fan motor and new 7.5 capacitor
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-717D-9F101F4768544C27BCE53C9223B17319
Upon inspection I found the 220v outlet for air handler did not have power. I could not find the breaker that goes to it. There was another 220v plug in the closet and I plugged it into that one. System is working properly at this time.
Upon arrival I found the unit was turned off. turned the unit on and nothing came on. Looked at the disconnect the disconnect was turned to the off position flipped it around and turned it on the unit turned on and it’s running within spec at this time. Homeowner thinks the neighbors kids might’ve messed with it. Advised her she could get a lock and put it on the disconnect.
Water heater comes with a 6 year labor warranty. 1. Remove and dispose old water heater. 2. Rebuild platform with plywood and sheet metal. 3. Supply and install new water heater. 4.Supply and install any copper fittings needed.
To help best longevity of the unit
2 ton Daikin package heat pump Single stage compressor System comes with a 12 year parts warranty. 2 year labor warranty through All Out. Scope of Work 1. Remove & Replace existing package heat pump system with new AHRI rated package heat pump system. 2. Crane Included for Installation. 3. Supply & Install new service disconnect & electrical whip. 4. Supply & Install new double pole breaker at electrical panel. 5. Supply & Install new insulated elbow. 6. Supply & Install new painted angle iron stand. 7. Supply & Install new thermostat control 8. Supply & Install new primary drain p-trap and test for proper operation. 9. Disposal and haul away of existing equipment per E.P.A. guidelines. 10. Process applicable utility rebates. 11. Register equipment to activate extended warranties. 12. Final site visit by Install Manager for performance and quality review.
On arrival found TXV not opening all the way causing restriction on refrigerant TXV and filter dryer need to be replaced including estimates on a re build package customer would like a quote on wensday later side of the day called trane and found that the parts would not be available for 3 to 4 weeks due to needing to have them shipped in
Air conditioner repair service call: Upon arrival found the unit is low on refrigerant. It appears they have a refrigerant leak. We are presenting three different options. option one is just putting refrigerant back in the unit. option two is filling the unit up with refrigerant and doing a leak search to pinpoint where the leak is and see if it can be fixed. option three is doing a condenser rebuild package along with a leak search to see if the leak is able to be fixed or not. We have George coming out Monday morning to give replacement options for the two older units.
Upon arrival found thermostat at 74 degrees. Checked full operation of equipment and found system in need of maintenance due to dirty outdoor coil and plugged drain line. Maurice approved addition of clean out to drain line. Added clean out and cleared plugged drain line. System has had a draining issue for a long time and rusted out secondary drain pan. Recommend replacing rusted drain pan to eliminate the possibility of drywall damage in the future. Air handler in attic has no return plenum. Recommend adding return plenum proper air flow and longevity of equipment. (See estimate) system now cooling properly and draining properly. Please contact Maurice with maintenance agreement details in writing.
Cleaned dry dirty indoor coil. System now cooling correctly. Spoke with clients and they are interested in adding a return. There is no attic space so all duct work will need to be added on roof. Will speak to george about addition of return and get back to customer. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-FF01-62D97E1C3C374CBEB76BCDE369520560
Upon arrival found thermostat was turned off. Turn thermostat on and on into cooling the unit turned on. From there tested all capacitors motors and refrigerant levels everything is checking out and is cooling within spec at this time.advise customer that the unit is cooling went inside the house verified Vents are cooling. unit within spec.
Installed fan blade on condenser fan motor and checked operation. Fan motor now working properly and balanced properly.
Upon arrival gained roof access and found compressor leaking oil and very loud while overamping. This is a package unit on the roof R22 system. The model number is not available but could see the serial number and the unit is from 2007. Due to age and condition we recommend George come out and give replacement system options. Will speak with George and Josh about replacing the compressor.
Found outdoor fan leaking oil and not working correctly. This is causing the system not to work correctly. Current time is 7pm august 31, supplier closed currently. Will follow up with supplier and client to schedule repairs tomorrow. See attached photos Returned to replace outdoor fan and capacitor that failed. Replaced and checked operation. Found outdoor fan out of balance likely causing original motor to fail prematurely. System cooling at this time but will need to order fan blade and return to replace and check operation. Covered under warranty. Recommend adding surge protector at disconnect on roof. See estimate for details.
Upon arrival found dual cab hermetic side was melted not letting the compressor turn on change out the capacitor and it’s not running and cooling within spec at this time
Upon arrival found bad capacitor. checked all pressures checked everything elseon the unit. the capacitor wasn’t allowing the fan motor to turn. replaced with new capacitor. unit is now running within spec. checked all refrigerant levels as well.
Upon arrival found the dual run capacitor was bad replaced with a new door run capacitor unit is now running within manufacture specs at this time
Thank you, Eileen! We think Ben is pretty great too!
Thank you, Abraham! Thank you for choosing All Out Cooling & Heating to repair your AC.
Thank you, Matt!
Kevin, we're thrilled to hear that George provided great service and was able to quickly get you cooling again! Thank you for this great feedback, we appreciate you!